10 Tips for Easy Cooling Tower Maintenance
Follow these 10 simple maintenance tips to get the most out of your cooling equipment:
1. Check the overall condition of the unit and listen for any uncommon noises to establish a baseline of any potential issues2.Before beginning any work be sure to follow proper lock out procedures and disconnect motor switches to ensure your safety3.Inspect and clean debris from strainers to keep the system free of excess materials.4. Inspect the water distribution system and check for dry areas over the fill coil section to avoid scale build up and increase system capacity. If the surface is not fully wetted check the nozzle for cracks and clogs5. Flush dirt and debris from the cold-water basin through the tower drain or sump strainer to maintain water filtration and keep dirt from collecting.6. Installing basin sweeper piping in addition to a filtration system will function as automatic maintenance7. Check the make-up water supply for the appropriate pre-determined water level to conserve water and reduce air8. Fix any tension problems on the belt to ensure optimal belt drive system performance9. Check oil level, oil quality, and shaft alignment for a gear drive system following the manufacturers’ recommendations10. Lubricate fan shaft bearings every 3 months at a minimum to maintain proper orientation. Installing BAC’s unique automatic bearing greasers is easy and can eliminate monthly bearing maintenance
Maintenance frequency varies depending on the condition of the circulating water and the environment in which the unit operates. Good maintenance habits will prevent equipment failure and extend equipment life. Storing critical parts in the inventory will also help reduce downtime in the event of an emergency. Save time, money, and energy with these 10 easy tips and get the most out of your cooling equipment.